COMPACT FIRE CURTAIN CONSTRUCTION
The fire curtain will remain retracted within its headbox until it is activated by heat exceeding 74°C in the vicinity of the fusible link. The speed of descent will be within the range of 0.15m/s to 0.3m/s and is compliant to AS1905.2.
Testing is by disengaging or activating the fusible link. To restore the Vii® Cabin the barrel assembly is required to be manually wound to its top position and a new fusible link installed.
Full scale and full assembly fire testing to AS1530.4 providing fire integrity up to 2 hours.
No need to fire protect the headbox or side guides as the complete product is fire rated. Assessment report CSIRO FCO-3071.
For Further Reference please read the documents provided below. If you wish to obtain further information regarding our Fire and Smoke protection, please contact us at (02) 9526 3100, or email us at email@example.com.
Alternatively, you can speak to us in person at Greene Fire Pty Limited, Unit 2 7-11 Parraweena Road Taren Point, NSW 2229
- No power, alarm signal or control equipment
- Preassembled system allows for fast installation
- Rapid ore regulated descent
- Light weight and compact solution is more aesthetically pleasing than shutters or doors
- Cost effective solution